Failed Jumper Sleeve
A jumper sleeve failed on a new construction project, causing a line to operate.
A raptor built a nest in infrastructure.
This photo shows broken conductor strands.
Livestock caused damage to a wood pole.
Issue on New Construction
During a new construction project, a conductor shoe made contact with an insulator.
This insulator has a broken bell.
Hole in a Pole
This pole sustained woodpecker damage.
Washed Out Foundation
The tower foundation was washed out.
The crossarm brace is broken.
Spotlight on Static Wire
This photo shows an eccentric alignment of static wire attachment.
The polymer insulator melted due to a hot conductor sleeve.
The pole top cover sustained damage, the hardware was rusted and a woodpecker created a hole in the pole.
Missing Cotter Key
During a new construction inspection, a cotter key is found missing.
The insulator attachment pin has a cotter key missing and the pin is backed out.
Grips With a Gap
During a new construction inspection, the conductor cushion grips have an excessive gap. They are likely not tight enough or the incorrect size for the conductor.